Temp. and Humi. Control
Particular Filter Application
Smart ESCO Control
|1.Pre-Air Washer (Particle Removal)|
|2.Bio Filter (90% Virus & Bacteria Suppression)|
|3.Pre-cooling (hot) Coil (AMC Removal Elevating)|
|4.AMC Air Washer (>90% Water-soluble AMC Removal)|
|5. Pre-cooling Coil|
|6. Re-Heating Coil|
|8.Chemical Filter (VOC &MA/MB Removal)|
|9.HEPA Filter(email@example.com Particle)|
|Item||Spray / Nozzle Type Air-washer||High-adsorption Clean Air-washer|
|AMC Eff.||NH4+ > 90%@ < 5ppbv||NH4+ > 90%@ < 3ppbv|
|Specific surface area(m2/m3)||115||400|
|Power Running Cost (ratio)||100%||4%|
|Advantage||1.Lower expense of setting up than high-adsorption Clean washer.|
2.Stainless steel Packing will not be a Amine clogged status happened.
|1.The air is passed through wet-modal in long time, and provides perfect humidifying.|
2.It is air contact area of water bigger than Nozzle type Air-washer, and removing AMC better than Pump-system.
3.low liquid-gas ratio, no pump with water circle, and low expense of operation.
|Disadvantage||1.Nozzle with the high-pressure forms water ring, so pump is high electric power and expense of operation.|
2.Nozzle be a Amine clogged status will decrease removal efficiency.
|1.The set cost is higher than Nozzle Type system.|
2.Ion adsorption pad could be Amine clogged status.